# AC DC Full Load Current Calculation Formula

## Full Load current calculation of AC and DC machine:

Full Load Current is nothing but a maximum allowable current. The input current to the machine exceeds the full load current means, the electrical machine may get damage. Due to the excess current flow, the machine produces additional heat (Because of P=I2 * R)., This may lead to damages to the insulation or winding of the electrical equipment. Hence, Operating a machine below full load current increases the life span of the electrical equipment.

#### Full Load current calculation 3 Phase Motor:

In most of the Three-phase systems, electricity consumption happens through star and delta connection. The input power (P) to the system is the same, irrespective of the connection.

Also Know About:   Electrical Panel & Types of Electrical Panels used In Industry

Power in KW (Kilowatts)

V= Voltage +/- 10 % in Volts

I= Full load current in Amps

Cos pi = power factor

`Three Phase Power P = 3 V*I* Cos pi`

KW = output power in Watts……. All are given at the nameplate details.

As we said, the full load current of the three-phase system is depending on the type of connection.

Here

Iph => Phase Current

Iline => Line Current

For Star Connection the Full Load Current Iline is equal to Iph

`Iph = Iline`

For Delta Connection the Full Load Current Iline is equal to 1.732 times of Iph

`Iph/1.732 = Iline`

Hence Three Phase full load current I is equal to

`I= P/(1.732*V*Cos pi)`

#### Full Load current calculation Single-phase Motor:

`P = V * I * Cos pi`

V= Voltage +/- 10 % in Volts

I= Full load current in Amps

Cos pi = power factor

KW = output power in Watts……. All are given at the motor’s nameplate details.

• `I =P / V * cos pi Amps`

#### Full Load current calculation Three-phase Heater coil:

Power formula  KW

Also Know About:   Identification of Motor Frame Size 132M & Motor EFF class EFF1 EFF2

V= Voltage

I= Full load current in Amps

KW = output power in Watts……. All are given on the heater’s plate details.

• `Iinput =P / 1.732 * V * I Amps.`

### Full Load current calculation Single phase heaters:

Power formula  KW

V= Voltage

I= Full load current in Amps

KW = output power in Watts……. All are given on the heater’s plate details.

• `I = V X I Amps`

Calculate through resistance:

1. Measure the resistance R of the heater coil using multi meter.
2. Use this formula

P = I^2 * R

• I = square root of (P/R)

Also see: How to Calculate Voltage Drop

#### Full Load current calculation DC machine (DC Motor & DC generator):

DC => Direct Current

`P= V X I`
• I = P/V amps, Where

V = E ± Ia Ra ± Is Rsh + brushes drop (shunt machine)

V = E ± Ia (Ra + Rsh) + brushes drop (series machine)

V = Supply Voltage

E = back emf

Ia = armature current

Ra = armature resistance

Is = Field current

Rsh = Field resistance

`Back EMF e = (pi * N * P * Z / 60 A)`
Also Know About:   What is Step potential and Touch Potential and Calculation

P = number of poles

Z = number of conductors

A = number of parallel paths

P = A for lab winding

A= 2 for wave winding