What is Step potential and touch potential and Step potential and touch potential calculations
Step Potential and Touch Potential:
Step Potential is nothing the potential developed between the two feet on the ground of a man or animal when short circuit occurs. Due to this potential the living body may get electric shock. This is mostly occurring in Electrical switch yard.Get More Electrical Concept And Interview Questions By Using This Link
Touch potential is nothing but a potential is developed between living body touches the faulty structure. When operating personnel touch an electrical equipment during short circuit condition, fault current flows through the human body.
To avoid this, we use stone on the high voltage switch yard and Transformer yard.
Step potential and touch potential calculations
According to the inputs for three-phase system:
Let us consider on the spread sheet for calculating touch potential and step potential. Please put the
|Line-to-Neutral Volts (Vn)|
|Line 1 Calculated Load (A1)|
|Line 2 Calculated Load (A2)|
|Line 3 Calculated Load (A3)|
|Service Neutral Impedance Z1|
|Ground Resistance (3-point method) R|
For single-phase systems input parameters are:
Circuit voltage and ampere,Touch-Voltage-and-Ground-current-22-8-12 load, ground, electrode and body resistance.